Inscrit le: 22 Avr 2018
|Posté le: Dim 6 Mai - 10:06 (2018) Sujet du message: Has anyone had equipment sabotaged by another service compan
OK, showed up on a contract customer's site to PM 2 chillers. Owner states one chiller had bad a bad board and the local rep was there to look at it under warranty a week or 2 prior to me showing up. The other chiller tripped out on low evap pressure. Long story short, found actuator on liquid line indexed wrong so the valve would only open 1/2 way. Chillers are 2 years old. Found paint chipped off on nuts and bolts at the actuator. There is no way it slipped or anything. This was deliberately done. When speaking to the owner about the problem, I stated that I didn't want to point fingers but this was done by SOMEONE. I talked to any of our techs that might have been there. No one touched it. This chiller never had any problems with this valve/actuator. I was there to look over job just after completion.Have any of you guys ran into situations like this and how did you handle it?
I didn't find the right solution from the Internet.
2D Promo Video